To troubleshoot a Napoleon gas fireplace that will not stay lit, check the drip loop, the pilot light, the thermocouple and the gas valve to ensure all components are clean and working before replacing. If the gas fireplace pilot light will not stay lit, troubleshooting common problems can usually fix this issue.Continue Reading
To troubleshoot the common problems of a gas fireplace not staying lit:
From your gas meter, check the drip loop for excessive moisture. Open the cap and drain any accumulated moisture from the drip loop.
The tiny metal rod above the pilot light is the thermocouple. Check to see that it is hitting the pilot light and that it is tightened into place.
Below the pilot light is the burner which has small holes that may become clogged. Clean the burner to remove carbon build-up by blowing out with an air compressor or washing with soap and water.
If previous troubleshooting does not remedy the problem, you may need to replace the gas valve.
A Dearborn heater might fail to light because of a corroded pilot tip, the size of the flame, insufficient gas or a bad thermocouple. Finding out the reason is essential to repairing the heater quickly.Full Answer >
Test a gas valve thermocouple by attempting to light the pilot, holding the pilot button and releasing it to see if the light goes out, which normally indicates a nonfunctioning thermocouple. Homeowners may also remove the thermocouple to perform a closed circuit test using a multimeter and a thermocouple adaptor.Full Answer >
A gas thermocouple works by creating a small amount of electricity that is sufficient enough to keep open the part of the gas valve that lights the pilot assembly. It acts essentially as a sensor which is connected to the main control valve.Full Answer >
According to HowStuffWorks, the thermocouple in a gas furnace uses two dissimilar metals that produce an electric current when heated in order to power an electromagnet that opens a valve allowing gas to reach the furnace. If the pilot light goes out, the thermocouple cools and no longer produces the current, so the electromagnet releases the valve to stop the gas flow.Full Answer >