A chimney is a system for venting hot flue gases or smoke from a boiler, stove, furnace or fireplace to the outside atmosphere. They are typically almost vertical to ensure that the hot gases flow smoothly, drawing air into the combustion through the chimney effect (also known as the stack effect). The space inside a chimney is called a flue. Chimneys may be found in buildings, steam locomotives and ships. In the US, the term smokestack (colloquially, stack) is also used when referring to locomotive chimneys. The term funnel is generally used for ship chimneys and sometimes used to refer to locomotive chimneys.. Chimneys are tall to increase their draw of air for combustion and to disperse pollutants in the flue gases over a greater area so as to reduce the pollutant concentrations in compliance with regulatory or other limits.
The term chimney may also be applied to natural features, particularly in rock formations.
In the eighteenth and nineteenth centuries, the methods used to extract lead from its ore produced large amounts of toxic fumes. In the north of England, long near-horizontal chimneys were built, often more than 3 km (2 mi) long, which typically terminated in a short vertical chimney in a remote location where the fumes would cause less harm. Lead and silver deposits formed on the inside of these long chimneys, and periodically workers would be sent along the chimneys to scrape off these valuable deposits.
In fact, many modern high-efficiency heating appliances do not require a chimney. Such appliances are typically installed near an outside wall, and a noncombustible wall thimble allows vent pipe to be run directly through the outside wall.
Industrial chimneys are commonly referred to as flue gas stacks and are typically external structures, as opposed to being built into the wall of a building. They are generally located adjacent to a steam-generating boiler or industrial furnace and the gases are carried to it with ductwork. Today the use of reinforced concrete has almost entirely replaced brick as a structural component in the construction of industrial chimneys. Refractory bricks are often used as a lining, particularly if the type of fuel being burned generates flue gases containing acids. Modern industrial chimneys sometimes consist of a concrete windshield with a number of flues on the inside. The 300 metre chimney at Sasol Three consists of a 26 metre diameter windshield with four 4.6 metre diameter concrete flues which are lined with refractory bricks built on rings of corbels spaced at 10 metre intervals. The reinforced concrete can be cast by conventional formwork or sliding formwork. The height is to ensure the pollutants are dispersed over a wider area to meet legislative or safety requirements.
A chimney cap is placed on top of the chimney to prevent birds and squirrels from nesting in the chimney. They often feature a rain guard to keep rain from going down the chimney. A metal wire mesh is often used as a spark arrestor to minimize burning debris from rising out of the chimney and making it onto the roof. Although the masonry inside the chimney can absorb a large amount of moisture which later evaporates, rain water can collect at the base of the chimney. Sometimes weep holes are placed at the bottom of the chimney to drain out collected water.
A chimney cowl or wind directional cap is helmet shaped chimney cap that rotates to align with the wind and prevent a back draft of smoke and wind back down the chimney.
A chimney damper is a metal spring door placed at the top of the chimney with a long metal chain that allows you to open and close the chimney from the fireplace.
In the late Middle Ages in Western Europe the design of crow-stepped gables arose to allow maintenance access to the chimney top, especially for tall structures such as castles and great manor houses.
When coal, oil, natural gas, wood or any other fuel is combusted in a stove, oven, fireplace, hot water boiler or industrial furnace, the hot combustion product gases that are formed are called flue gases. Those gases are generally exhausted to the ambient outside air through chimneys or industrial flue gas stacks (sometimes referred to as smokestacks).
The combustion flue gases inside the chimneys or stacks are much hotter than the ambient outside air and therefore less dense than the ambient air. That causes the bottom of the vertical column of hot flue gas to have a lower pressure than the pressure at the bottom of a corresponding column of outside air. That higher pressure outside the chimney is the driving force that moves the required combustion air into the combustion zone and also moves the flue gas up and out of the chimney. That movement or flow of combustion air and flue gas is called "natural draught/draft", "natural ventilation", "chimney effect", or "stack effect". The taller the stack, the more draught or draft is created.
Designing chimneys and stacks to provide the correct amount of natural draught or draft involves a number design factors, many of which require trial-and-error reiterative methods.
As a "first guess" approximation, the following equation can be used to estimate the natural draught/draft flow rate by assuming that the molecular mass (i.e., molecular weight) of the flue gas and the external air are equal and that the frictional pressure and heat losses are negligible:
|Q||= chimney draught/draft flow rate, m³/s|
|A||= cross-sectional area of chimney, m² (assuming it has a constant cross-section)|
|C||= discharge coefficient (usually taken to be from 0.65 to 0.70)|
|g||= gravitational acceleration, 9.807 m/s²|
|H||= height of chimney, m|
|Ti||= average temperature inside the chimney, K|
|Te||= external air temperature, K|
Other problems include "spalling" brick, in which moisture seeps into the brick and then freezes, cracking and flaking the brick and loosening mortar seals.
In some cases the chimneys of power stations are used also as pylons. However this type of construction is not very common, because of corrosion problems of conductor cables.
|GRES-2 Power Station||1987||Kazakhstan||Ekibastusz||420 m||1378 ft||Tallest chimney in the World|
|Inco Superstack||1971||Canada||Copper Cliff||385 m||1263 ft||Tallest chimney in the Americas|
|Trbovlje Chimney||1976||Slovenia||Trbovlje||360 m||1181 ft||Tallest chimney in Europe|
|Anaconda Smelter Stack||1919||USA|| Anaconda,|
|178 m||585 ft||Tallest freestanding brick chimney|
|The Windscale Pile Chimneys||1957||UK|| Windscale,|
|124m||406ft||Tallest nuclear plant chimney and site of world's first reactor accident|